SPS-M48 Power Supply Manager is designed for distribution of DC Power Supply from Power Supply Units (PSU) and a back-up battery. The unit controls battery charging and distributes power supply to all Voice Evacuation System (VES) equipment at max 60 A. When the system uses battery backup, the power supplied is 3.2 kW (48 V) and 1.6 kW (24 V). The unit complies with the EN 54-4 VES standards and also EN 12101-10 Smoke and Heat Control System standards.
As a main source of energy distribution, the manager uses external modules 800 W (SPS-48800) for 48 V. PSM48 power supply manager uses internal power converter for 24 V equipment. As a source of stand-by power supply it uses the battery bank of the capacity of up to 200 Ah.
SPS-M48 cooperates with the 4×12 V VRLA battery bank. It maintains the bank in charged condition, ensures temperature compensation of charging parameters and monitors serial resistance of the battery and its wiring as specified in Exhibit No. A2 to the EN 54-4 Standard.
SPS-M48 co-operates with up to 4 modules of SPS-48800 Power Supply Units. The manager ensures safe connection for the purpose of parallel operations and monitors the output parameters of each power supply unit.
SPS-48800 is designed for assembling in a dedicated SPS-F4 Power Supply Unit Frame. The elements of the system are designed for assembling in a Rack 19” IP30-type.